IEEE Std ™). IEEE Recommended Practice for. Insulation Testing of AC Electric. Machinery ( V and Above). With High Direct. IEEE Std 95 () IEEE Recommended Practice for Insulation Testing of Large AC Rotating Machinery with High Direct Voltage. (This foreword is not a part of IEEE Std , Recommended Practice for Insulation In the Insulation Subcommittee of the IEEE Rotating Machinery .
|Published (Last):||12 March 2012|
|PDF File Size:||12.2 Mb|
|ePub File Size:||9.34 Mb|
|Price:||Free* [*Free Regsitration Required]|
Examples of stator winding partial discharges due to inverter drives.
On-line and off-line tests M. Significance of defects found during high direct voltage ramp tests. This last scenario was also useful to test extrapolation accuracy.
Stone Published in IEEE Transactions on Industry Applications IEEE standards and test procedures are widely used by motor and generator vendors and users to commission windings in new machines, as well as evaluate the condition of the winding insulation in operating machines. Diagnostic tests Interpretation logic R. Ieer Research An Academic Publisher.
Adrian Segall – Google 学术搜索引用
Power uprates pose a threat to electrical generators due to possible parasite effects that can develop potential failure sources with catastrophic consequences in most cases. This paper has 48 citations. References Publications referenced by this paper. Detection of stator winding insulation failures: Since the s, motor windings have encountered many changes in their design and manufacture.
National Institute of Technology | Warangal
Uniform step, graded step, and ramped test methods. World Journal of Engineering and TechnologyVol. Topics Discussed in This Paper. High – voltage DC tests for evaluating stator winding insulation: Until recent revisions, the basic procedures and standards in use were written over 25 years ago.
Skip to search form Skip to main content. The mathematical model developed was based on an artificial intelligence technique, more specifically neural networks. Ifee method is applied to determine core-end temperature when power is uprated to From This Paper Figures, tables, and topics from this paper. Online technique for insulation assessment of induction motor stator windings under different load conditions Majid MalekpourB.
Showing of 39 extracted citations.
Army Engineer Manual Engineering and Design Hydroelectri
Showing of 7 references. Dhirani, Electrical Insulation for Rotating Machines. Use of AC and DC hipot tests to assess stator winding insulation. In that sense, it is important to pay close attention to overheating, which results from excessive system losses and cooling system inefficiency.
At that point, the temperature value will be compared to with the values obtained using finite elements method and multivariate regression. The calculation of magnetic fields, the evaluation of eddy-current losses and the determination of loss-derived temperature increases, are challenging problems requiring the use of simulation methods. The most usual methodology is the finite element method, or linear regression. Understanding water treeing mechanisms in the development of diagnostic test methods.